Arc Furnaces 15 to 46 kV and Greater Than 15 MVA
|Number of Switches Per Phase||Control Transformer||Control Voltage||Control Part No.|
|1||5 KVA at 3.5% max impedance or 10 KVA at 7% max impedance||120 VAC||1001711G13|
|2||10 KVA at 3.5% max impedance or 20 KVA at 7% max impedance||120 VAC||1001712G13|
|3||15 KVA at 3.5% max impedance or 30 KVA at 7% max impedance||120 VAC||1001713G13|
|4||20 KVA at 3.5% max impedance||120 VAC||1001714G13|
|5||25 KVA at 3.5% max impedance||120 VAC||1001715G1|
|6||30 KVA at 3.5% max impedance||120 VAC||1001716G1|
The control to the left is for an arc furnace with 3000 amperes primary current at 15 kV or 1500 amperes at 34/46 kV. It can operate nine switches total or three per phase. It is a direct replacement for a Joslyn™ arc furnace control. The control shown is representative of a whole range of controls available which are capable of operating from three to eighteen switch mechanisms. The control is modular for easy diagnosis and repair.
This control can minimize transient in-rush current either with resistor insertion switches or synchronous closing with the alternating current sine wave.
The control is operated by an Allen Bradley™ MicroLogix™ 1100 PLC. The PLC has diagnostics built into its PLC program. The control can detect a switch mechanical malfunction and initiate an emergency trip so as to prevent single phasing of the furnace transformer. Single phase power on a furnace transformer is a frequent cause of exploding arrestors.
The control has a reset function which can reset the control following an intermittent switch malfunction. This feature enables a furnace to continue operating without down time while deferring the maintenance on switches to a convenient down day.
The MicroLogix™ PLC has an Ethernet connection for remote monitoring with a PanelView™ monitor. The PanelView™ monitor graphically displays individual switch open or closed status and maintains a date and time stamped log of switch malfunctions which resulted in the control being reset.
Back to Switch Controls